Easy Removing and Refixing even by a layman makes it a perfect choice for High maintenance areas and open -office-plan of larger area. Panel size can be defined exactly as of Light/Diffuser size giving it a perfect flush look. Exposed Grid System mixes Linear and Akostisil looks along with possibilities of colour combination with carrier (“C” patta) of different colour. Plain carrier and perforated panel break the monotonous look of either plain or perforation.
Technical Specification (PLANK 1249mm X 286mm)
Manufacturers Specification for 1249 * 286 mm Concealed “PLANK” Perforated / Plain Panel False Ceiling System.
Panel Details (Aluminium)
Panels shall be fabricated from 0.71 mm thick (TCT) aluminium Sheet. Panel shall be square edged. Panel size shall be 1249 mm * 286 mm and shall be powder coated on external surface only. Edge profile shall be 18 mm * 20 mm fabricated from G.I. Sheet.
Panel Details (Galvanized Steel)
Panels shall be fabricated from 0.50mm thick (TCT) G.I. sheet. Panel shall be square edged. Panel size shall be 1249 mm * 286 mm and shall be powder coated on external surface only. The edge profile shall be 18 mm * 20 mm fabricated from G.I. Sheet.
- Tile shall have 1.6 mm dia at 3 mm Centre to Centre in diagonally
- Tile shall have 2 mm dia at 7 mm Centre to Centre in diagonally
- Tile shall have 2.5 mm dia at 5 mm Centre to Centre in square pattern
- Tile shall have 3 mm dia at 7 mm Centre to Centre in diagonally
- Tile shall have 6 mm Square holes at 12 mm Centre to Centre in Square Pattern
Suspension and Installation Details
The Carrier 75/100 mm in width shall be fabricated GI sheet thickness 0.45 mm shall installed to each other, with the help of 75/100 mm width Hold on Hanger, GI Rod 4 mm dia shall be screwed to slab, spacing of Suspenders shall be max. 1200 mm and shall be fitted to Hold on Hanger with Height adjustment suspension clip. The spacing between the carriers shall be 1324/1349 mm centre to centre and the flanges at each end of the plank shall rest on the top of the exposed carrier. Perimeter clip shall be provided at wall periphery fabricated from GI sheet. Pressure clip shall be provided along the length to hold the Panels.
GI rod, top and bottom portion of rod shall be rounded, Top end shall be screwed to slab and bottom shall be nut bolted to hold on hanger. Sil Carrier shall be fixed into hold on hanger with level adjusting spring steel clip to maintain the desired level of False Ceiling. Suspenders shall be at max. 1200 mm and the distance between two carriers will be 1249 mm center to center. Panel shall be snapped into carrier. Pressure clip shall be provided along the length to hold the panels. Edge profile shall be fixed on the perimeter of walls and columns.