CLIP IN (SIL) (600 X 600)
The entire ceiling assembly has no visual suspension runners providing a clean unobstructed visual appearance. Clip in Square tiles in patterns of perforations and colours in different lay out this ceiling an uncomparable Aesthetics.
Clean Room Application:
Pharmaceuticals and medical device manufacturing requires sterile environment with cleanliness levels varying from class 100 to class 10000.
The smooth polyester powder coating face does not attract dust and do not encourage the growth of micro organisms. After the ceiling has installed, the seal provided by Silicone Sealant, Tape or Gasket should prevent any possible contamination from the edges from entering the clean room.
Technical Specification (600mm X 600mm)
Manufacturer Specification for 600 * 600 mm Concealed Plain / Perforated Panel False Ceiling System.
Panel Details (Aluminium)
Panels shall be fabricated from 0.71 mm thick (TCT) aluminium alloy (AA) 8011 – H3. Panel shall be square edged. Panel size shall be 600 mm * 600 mm and shall be powder coated on external surface only. Edge profile shall be 18 mm * 20 mm fabricated from G.I. Sheet.
Panel Details (Galvanized Steel)
Panels shall be fabricated from 0.50mm thick (TCT) G.I. sheet. Panel shall be square edged. Panel size shall be 600 mm * 600 mm and shall be powder coated on external surface only. The edge profile shall be 18 mm * 20 mm fabricated from G.I. Sheet.
- Tile shall have 1.6 mm dia at 3 mm Centre to Centre in diagonally
- Tile shall have 2 mm dia at 7 mm Centre to Centre in diagonally
- Tile shall have 2.5 mm dia at 5 mm Centre to Centre in square pattern
- Tile shall have 3 mm dia at 7 mm Centre to Centre in diagonally
- Tile shall have 6 mm Square holes at 12 mm Centre to Centre in Square Pattern
Suspension system shall be consist of G.I. rod 4 mm dia, GI Hold on hanger 1.15 mm thick of height 95 mm * 12 mm, GI Sil Carrier 0.45 mm thick 25mm * 2440mm, GI Pressure clip 1.20 mm thick 35 mm * 30 mm, Powder coated Spring steel clip 0.50 mm thick and Powder coated 0.5 mm thick GI Edge Profile.
Top and bottom portion of rod shall be rounded, Top end shall be screwed to slab and bottom shall be nut bolted to hold on hanger. Sil Carrier shall be fixed into hold on hanger with level adjusting spring steel clip to maintain the desired level of False Ceiling. Suspenders shall be at max. 1200 mm and the distance between two carriers will be 600 mm center to center. Panel shall be snapped into Sil Carrier. Pressure clip shall be provided along the length to hold the panels. Edge profile shall be fixed on the perimeter of walls and columns.